- Supports 2 hardwired zones for intrusion and fire types of detectors;
- Status LED for each zone;
- 2 built-in "dry output" relays;
- Powering from mains power network;
- Supports relay units Astra-821, indication units Astra-861;
- Supplying active detectors and other devices with 12V supply voltage.
- ARM/DISARM using Touch Memory (DS1990A) keys (iButton).
- Memory for up to 28 iButton keys for ARMING/DISARMING;
- Intrusion and fire alarm type hardwired zones;
- Power output 12 V for suppluying the hardwired detectors;
- Configuration of operating modes using jumpers.
|Power from mains power network||187 - 242 V AC|
|Power from rechargeable battery (form factor 7 A/h)||12 - 14 V DC|
|Voltage on the hadwired zone terminals (for suppluying detectors)||9 - 14 V DC|
|Hardwired zone short circuit current||20 mA|
|Intrusion type zone integration time||70+-10 msec|
|Fire alarm type zone integration time||300+-30 msec|
|Hardwired zone resistance:|
|Norm||3 to 5 kOhm|
|Alarm||0 to 3 and more than 5 kOhm|